SA501 wire connection is a 12V DC with feedback function.
Details of the connections are as follows
- Keep your 12V 1.5Amps power supply ready.
- Connect the 12V DC +ve to the Red colour wire.
- Connect the 12V DC -ve to the Black colour wire.
- Connect the Green wire to the 12V +ve whenever the valve needs to be opened.
- This supply to the green wire can be given thru PLC, Relay Float switch.
- As long as you need to open the valve, the green terminal should be connected to +ve 12V DC.
- Note: Since the valve is stay put on power failure type. Red and black to be connected to positive and negative of 12V DC always. Power consumption during valve close is zero and open is around 20mA. Actual power consumption takes during the movement of valve.
- Feedback output can be taken from blue for open side and yellow for close side. Feedback voltage is +12V DC
Still can’t find an answer?
Send us a ticket and we will get back to you.